The image above is for illustration purpose only. The actual module may vary from the one presented here.
Module M-CON-232-s is a component of the Ampio system. Required voltage to power the module is 11 — 16V DC. The module is controlled via CAN bus.
The module allows for the integration of devices equipped with an RS-232 communication interface with the Ampio home automation system.
The module is designed for mounting on a 35mm DIN rail. The module’s width is 35mm, 2 spaces/modules in DB. In order to start the module, it must be connected to the CAN bus. The bus of the Ampio system consists of four wires - two for power and two for communication between the modules.
In addition to the CAN bus connector, the device has a connector that provides access to the Rx and Tx lines of the RS-232 interface.
In order to connect to an external device using the RS-232 interface, one must prepare a cable terminated with a connector suitable for the device that is being integrated. The device connection diagram presents a variant of such a connection with a short circuit of the DCD, DTR and DSR lines. Before integration, read the manual of the integrated device to see, if the connection is required by it.
On the front of the module there are signalling LED indicators. The green LED with the label CAN indicates the status of communication on the CAN bus:
Apart from the communication bus status LED, there are three red LEDs on the front of the device:
The nature of the communication error depends on the specialised firmware variant loaded into the device.
The module is programmed with a special programmer, available for authorised technicians, and the Ampio Smart Home CAN conﬁgurator software. It allows you to modify the parameters of the module and define its behaviour in response to signals directly available to the module as well as general information coming from all devices present in the home automation bus.
Due to the complexity of the implemented functionalities and the specialised nature of firmware, the M-CON-232-s module is one of the few devices that is not updated automatically. Uploading a new version of the software is possible only manually, i.e. by selecting an appropriate file with the software update.
Unlike most Ampio system modules, the M-CON-232-s module software is specialised, i.e. depending on the intended use case, an appropriate firmware must be loaded to the device.
Specialised software is identified by a file name, the syntax of which is mostly consistent with the adopted nomenclature for Ampio devices' update files. The only difference is that the last two digits of the software version define the purpose of the programme.
The M-CON-232-s module firmware’s file name takes the following form:
[PCB]is the numerical identifier of the module’s hardware platform version,
[VER]is the firmware version,
[TYP]is the two-character firmware specialisation code.
The table below presents the available variants of the M-CON-232-s firmware specialisation:
||INTEGRA||Integration with the Satel Integra alarm system.|
||UNI-ONEWAY||General purpose one-way integrations - sending of arbitrary commands.|
||WEKTA-INT||Integration with the Wekta system.|
The specialised software files are delivered with the Smart Home CAN configurator software.
Dimensions expressed in millimeters.
Click to enlarge and open in a new tab.